Condair CP3 Mini with Fan. CP3-PR Series with inbuilt fan for direct room applications, kg/hr. The ventilation FAN unit is used for direct room air. The CP3 is an electrode steam humidifier which represents the latest generation of proven electrode steam humidifiers. Using normal drinking. United Humidifiers – Offering Condair Cp3 Electrode Boiler Steam Humidifier in Mumbai, Maharashtra. Read about CAR HUMIDIFIER. Mini Humidifiers.
|Published (Last):||15 October 2018|
|PDF File Size:||8.80 Mb|
|ePub File Size:||9.41 Mb|
|Price:||Free* [*Free Regsitration Required]|
Please note the following: Detailed information on the different settings are found in the following chapters. If the inspection reveals any irregularities e.
On this occasion check the following: If the timer is activated, up to eight switching points events 1 – 8 with different capacity limits can be defined. Make sure, therefore, that the construction wall, pillar, etc.
Switch on the service switch for mains supply. Installing the condensate hose Important! Unit switch lights and the standard operating display is shown. Maintenance Humidity sensor signal signal Y missing ——— Warning W No sensor signal present at signal input signal Z. Broken No sensor signal present at signal input Signal Y. P Internal P controller Int.
Condair CP3 Mini low capacity steam humidifier
Qualification of personnel All actions described in the present mounting instructions must be carried out only by well trained and sufficiently qualified personnel authorised by the owner. If the unit is opened immediately after having produced steam there is danger of burning when touching the steam cylinder.
The reset dialogue shows up in the display. Electrical installation X X Check all cables in the unit are firmly positioned and examine status of insulation. Before putting the unit into operation, the siphon of the condensate hose must be filled with water. Off Set Controls Kini If the unit has to be switched off because of a malfunction, please note the error code of the actual error message shown in the display.
Foam Steam cylinder needs service yellow lights Warning W Components Interval I Steam cylinder type A. Safety Some maintenance work requires removal of the unit cover.
Off On, Off 4. It’s a community-based project which helps to repair anything. After confirmation, the unit automatically switches to the selected dialogue language. Safety loop open Max. To eliminate the malfunction see chapter 6.
Copyright protection The present operating instructions are protected under the Copyright Act. Release the hose clamp on the steam connector of the steam cylinder, then detach the steam hose from the steam connector.
The steam humidifier must be connected to the mains only after all mounting and installation work has been completed and the cover has been relocated properly. Rm mm DS22 12 m 0m 1 KS10 m m min.
If you have questions relating to the dimensioning of ventilation ducts in combination with steam humidifiers Condair CP3mini, contact your Condair supplier. Inlet valve X Remove and clean filter insert, replace if mnii. Further information on accessories can be obtained in the respective instructions. Behaviour in case of cpp3 If it is suspected that safe operation is no longer possible, then the Condair CP3mini should immediately be shut down and secured against accidental power-up according to chapter 4.
Maintenance Maximum operating hours of the steam Replace steam cylinder.