ULC is pleased to announce the publication of the Fifth Edition of CAN/ULC- S, Standard for. Inspection and Testing of Fire Alarm Systems. This National. Fire Alarm Inspection, Maintenance, and Service by Anubis Systems Technologies. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected.
|Published (Last):||6 October 2012|
|PDF File Size:||14.97 Mb|
|ePub File Size:||12.20 Mb|
|Price:||Free* [*Free Regsitration Required]|
Cabinets have no corroded or damaged parts? Alarm valves shall be inspected externally. The fire signal receiving centre transmitter is located remotely from the fire alarm control B unit.
Quick opening devices passed test? Foreign materials found in dry-pipe valves, check valves or pumps? Trouble signal silence switch operates. BB Main power to emergency power supply transfer operates. The fire alarm system has: Confirm field device protective dust shields or covers removed. Combination appliances individually inspected and tested. Fifth year inspection items. Your service agency MUST identify those detectors that it could not perform this test on.
Correction of any troubles should be left in the hands of a trained Anubis Systems Technologies fire alarm service technician.
Power for ancillary devices is taken from the control unit or transponder that is designed to provide such power. Defective intake screen for pumps taking suction from open sources? Interior of dry pipe valve cleaned? If housing discolouration is noted, attempt to a536 the source and note the date of manufacture.
Correct designations for common control functions and indicators.
Circuits for emergency telephone call-in operation, including audible and L visual indication operates. Hydraulic name plate is properly affixed to the sprinkler riser? Are above results comparable to previous tests?
CAN/ULC-S536-04 Fire Alarm Annual Inspection Test Form
Where possible, identify the date a fire detector is changed. Yes No Pump run for ten 10 minutes Test log reviewed via visual display at controller? Check relief port on pressure reducer valves are not leaking? Backflow prevention assemblies have been tested by an agency acceptable to the local authority?
G Confirm that the supervisory transmission to the fire signal receiving centre is received. Input circuit alarm and supervisory operation, including audible and visual indication R operates.
Audibility of alarm sounder checked? Multi-line sequential display operates as per Appendix C5. Pipe and fittings shall be inspected from floor level? This type of detector works best for fast flaming fires that produce small amounts of smoke.
If any of the following were discovered, was an obstruction investigation conducted ulcc the system flushed?
Standards Council of Canada
Valve supervisory switches tested? Manual activation devices passed test? Individual alarm and supervisory zone indication operates. Applying household voltage to the interconnection wire will result in the destruction of any connected alarms and may even cause a fire.
CAN/ULC-S Fire Alarm Annual Inspection Test Form
Annual Testing – The Annual Test of the fire alarm system is performed by qualified technical personnel to a specific National Standard.
Extinguishing system controlled by fire alarm system?
Most house fires cab in the electrical wiring so it’s a good idea to have a battery operated smoke alarm installed as a “back-up”. Visual signal appliances individually inspected and tested.
The last inspection caan on the Certificate occurred on: Circuit Disconnect Means Location: Oil level in normal range on air compressor?
For homeowners with ten year old multi-station type smoke alarms or who may be contemplating changing or upgrading their existing units! Yes No NA Belt checked for proper tension?